Potential Annual Revenue
http://adult-literacy.net/?newenbinary=IQ-option-Hong-Kong&935=d5 IQ option Hong Kong
http://news.trafcom.com/?forexen=forex-trading-for-beginners-in-urdu&875=f9 forex trading for beginners in urdu
http://villasankofa.info/?forexen=info-forex-gold&ca4=3b info forex gold
Simplified Payback Analysis Cost Model
http://stsb.ch/?trading=forex-market-work-hours forex market work hours
- Based on estimated annual revenue per generating unit of $236,800 at 350 kW average annual output and $.077 per kWH pricing
- A single 5-Unit site operation would yield annual revenue of approximately $1,180,410.
- Site and Unit Installation Costs
- Costs include generating unit field installation, electrical interconnection equipment and construction, permitting, start-up costs, and the present value of ongoing O&M
- Grid interconnection iq option record equipment and installation costs are estimated to be $2,000,000 per site plus $1,000,000 per unit, or http://ferienwohnung-bloischdorf.de/?debinary=iq-Option&c47=ba iq Option $7,000,000 for a 5-unit site.
http://jollywear.com/?itbinary=broker-opzioni-binarie-rimborso&4a5=8a broker opzioni binarie rimborso
- The cost to produce and deliver each generating unit is estimated at $1,000,000 or $5.0 million for a 5-Unit site
- The total present value cost to install a five-unit site is estimated at $7 million
Simple EBITDA Payback
- Dividing costs by revenue produces a simple payback of 5.9 years
- Payback is highly sensitive to turbine efficiency, site development cost, generating unit cost, and site power production potential
- Research enabling effective design, fabrication, and construction of the generating unit will be a significant factor enabling financial success
Comparison of Competing Technologies
- Electrically, the units will be designed to produce 30kW to 350kW of power at 480 volt Direct Current (DC). The present design utilizes a commercially available inverter to convert the DC voltage generated to 3-phase Alternating Current (AC).
- The AC current is then stepped-up to the appropriate Distribution Line voltage (typically 12-13kV) using a commonly available transformer
- All electrical interconnecting components between the device and the Utility’s Distribution system will follow IEEE Standard 1547.
- This standard was issued in 2003 and is well established and in common use at this time.
- The interconnection components are identical to those used for wind and solar installations and are commercially available from multiple vendors serving the industry.
- System protection and control devices, communication protocols, and metering standards are also well-established and in common practice throughout the US.